Vent Rate Là Gì – What is a Vent Test? or what is a Ventilation Flow Rate Test?
Bài viết What is a Vent Test? or what is a Ventilation Flow Rate Test? thuộc chủ đề về Vent Rate Là Gì đang được rất nhiều bạn quan tâm đúng không nào !!
Hôm nay, hãy cùng internationalistreview tìm hiểu What is a Vent Test? or what is a Ventilation Flow Rate Test? trong bài viết hôm nay nhé !
Mời bạn Xem video Vent Rate Là Gì
Giới thiệu về What is a Vent Test? or what is a Ventilation Flow Rate Test?
Hi, I’m Paul Whiffin from at ATSPACE and today, we’re answering a question: “what is a vent test?” or what is a ventilation flow rate test? Ventilation is part F of the building regulations, and today we’re going to show you how we perform one, and this is for an intermittent fan, which is system one. Right. Well, I’m going to show you is the equipment we use these are the two hoods that we get the reasons for different sort of style hood is to fit over certain circumference of fans and to get into those tricky areas. And basically what hooks on the back, this gadget here straight in there is the anemometer. And this measures the flow rate of extraction. So, I’m going to show you what it looks like when we stick it over a fan.
So in here, we got utility. A small utility room. They got to achieve 30 litres a second in these small rooms due to all the appliances in them. Got to make sure the door has a gap underneath it so I can draw air in between 10and 12 mm. And the door should be shut when you’re testing. So, Anyway, let’s put it over the fan. Make sure it’s a nice fit. You got to give it a bit of time for it to pick up things so we can measure it. Make sure the fan is working well. We got 31.4. So this complies with the building regulations. Were going into the bathroom next. Each wet room. Whether its is a bathroom, WC, kitchen has different extraction rates. So bathrooms have 15 litres a second WC, which stands for water closet which tends to be sinks and toilets they have a extraction rate of 6. Kitchen extraction rate of 30. If the hob is adjacent to the fan is got to achieve 60 so got to be a bit careful with what size of fans you actually instal right again, the fan is on. Sounds like it’s working fine. Stick the hood over. This has to achieve 15 litres a second in the bathroom. And as you can see, and you can see that there we are achieving 15.4. This drops a little bit, due to the camera underneath it, there we go 15. So again, this complies with part F.What we do is we make a note of this, and we issue a certificate for building regulations to meet part F. And that you can submit your building control to get sign off. Thanks for watching the video if you like what you’ve seen, please like or subscribe and if you have any comments or questions, please put them below so I can help you further.
Tra cứu dữ liệu về Vent Rate Là Gì tại Wikipedia
Bạn nên tra cứu thông tin về Vent Rate Là Gì từ website Wikipedia.
Câu hỏi về Vent Rate Là Gì
Nếu có bắt kỳ thắc mắc nào về Vent Rate Là Gì hãy cho chúng mình biết nhé, mọi thắc mắc hay góp ý của các bạn sẽ giúp mình hoàn thiện hơn trong các bài sau nhé!
Bài viết What is a Vent Test? or what is a Ventilation Flow Rate Test? được mình và team tổng hợp từ nhiều nguồn. Nếu thấy bài viết Vent Rate Là Gì giúp ích cho bạn thì hãy ủng hộ team Like hoặc Share nhé!
Hình ảnh về Vent Rate Là Gì
Ảnh giới thiệu cho Vent Rate Là Gì
Tham khảo thêm những video khác về Vent Rate Là Gì tại đây: Nguồn tham khảo từ khóa Vent Rate Là Gì tại Youtube
Thống kê về video Vent Rate Là Gì
Video “What is a Vent Test? or what is a Ventilation Flow Rate Test?” đã có 1298 lượt đã xem, được thích 12 lần, chấm 5.00/5 điểm.
Kênh ATSPACE Ltd đã dành nhiều công sức và thời gian để hoàn thiện video này với thời lượng 00:03:33, các bạn hãy lan toả clip này để ủng hộ tác giả nhé.
Từ khoá cho video này: #Vent #Test #Ventilation #Flow #Rate #Test, Atspace,atspaceltd,ventilation Howtocarryoutaventilationtest,Vent Extractor Testing,Vent Testing,Vent Testing Building Regs,Extractor,Extractor Test Building Regulations,Extractor Ventilation Testing Part F,Building Regulations Ventilation Test, Vent Rate Là Gì, Vent Rate Là Gì, Vent Rate Là Gì, Vent Rate Là Gì, [keyword_title_words_as_hashtags]
Nguồn: Vent Rate Là Gì Tại Google